A boiler feed pump (BFP) driven off of the main steam turbine via a fluid drive was experiencing high vibration levels leading to frequent replacement of the fluid drive bearings. The plant depended on the single BFP for power production. Normal plant operation required the BFP and fluid drive output shaft to operate from 2000 rpm to 3500 rpm. MSI’s test results allowed the end-user to slightly modify plant operation in order to more reliably continue power production until permanent fixes recommended by MSI could be implemented during a future planned outage.
MSI’s field testing was a combination of impact modal testing as well as operating forced response testing. Data for each of these tests was acquired at approximately 125 locations on the fluid drive, pump, front standard, and foundation. The impact modal testing was used to determine the natural frequencies and mode shapes of the vibration while the plant operated. The operating forced response test data was used to produce the operating deflection shape (ODS) of the pump and drive assembly. A detailed ODS of the type that MSI performs shows the relative motion (amplitude and phase) of each portion of a structure at a given frequency, and typically provides valuable insight into the problem sources and their relative importance. MSI also used shaft rider sticks to investigate for a possible torsional natural frequency in the machinery train.
The operational testing indicated that the high vibration levels occurred at 60 Hz, and were primarily on the input end of the fluid drive and the front standard, peaking at a fluid drive output shaft speed of 2500 RPM (42 Hz). However, the vibration levels on the output shaft were much higher at 60 Hz than at 42 Hz. MSI concluded that the high vibration levels at 60 Hz were primarily due to a torsional critical speed of the rotor system, which was able to “tune in” to 60 Hz as a function of the amount of oil in the fluid drive. The torsional stiffness of the fluid drive controlled the output shaft speed, which is why the vibration level appeared to be related (but indirectly as it turned out!) to the output shaft speed. In addition, a structural natural frequency of the fluid drive bearing pedestals at about 64 Hz was clearly identified via ODS and modal testing. The rotor/ structural combined vibration led to severe deterioration of the foundation below the fluid drive to the point where the ODS and modal analysis animation showed that the sole plates were no longer integrally connected to the foundation, further magnifying the system vibration, as evidenced by the figure below. The bearing pedestal natural frequency and foundation separation amplified the overall system shaking at 60 Hz, but the torsional critical speed was the root cause of the problem.
An exaggerated-motion animation of the modal “bump” test performed while the pump train operates. Note the motion of the base of the fluid drive and sole plates relative to the concrete foundation, shown to be no longer intimately connected.
The plant had to remain operational, and therefore a long-term fix involving foundation was not a near-term option. To maintain power production, the customer used MSI results to establish a strategy of avoiding fluid drive operation at 2500 rpm to limit rapid bearing wear/ failure, and front standard deterioration. Permanent fixes to the foundation, along with modifications to the coupling or other shaft components to shift the problem torsional frequency, were laid out, and planned for a future outage.
A steam turbine at a waste-to-energy facility in the Northeast underwent a scheduled repair, at which time the turbine bearings were reworked, after which the turbine periodically experienced very high amplitude shaft vibrations.
A boiler feed pump (BFP) driven off of the main steam turbine via a fluid drive was experiencing high vibration levels leading to frequent replacement of the fluid drive bearings.
MSI was contracted to understand and help solve a high vibration problem on an aero-derivative gas turbine driven generator.